eNews & Articles
|Spon Water Consulting communicates pertinent issues regarding
industry news, upcoming workshops, technical innovation and
treatment updates to all of the clients it services on a
regular basis. We do so in a technical bulletin format which
we call “eNews”. You may receive future bulletins
by subscribing to eNews & Articles.
Spon eNews and Articles are distributed free via e-mail
to our clients and subscribers. You may preview a synopsis
of previous articles in PDF Format by clicking on the archived
article below. To receive the entire article or for rights
to publish in your trade journal contact Spon Water Consulting.
Iron (Fe) Fraction Analysis - 04/23/08
1. Total Fe: Analyze raw or finished water sample using Ferrover #8008 for total Iron.
2. Soluble Fe: Analyze raw or finished water sample using the 1,10 Phenanthroline Method #8146 to determine soluble iron. Soluble unbound (ferrous) iron can be sequestered with polyphosphate to prevent water discoloration, or to minimize iron color when corrosion occurs in the system. Sequestering iron at the water supply or in the system reduces chlorine demand and improves disinfection efficiency in the system, so as to control microbial regrowth and corrosion byproducts.
3. Oxidized Fe: Oxidized iron (ferric or bound) can be calculated by subtracting the soluble ferrous iron from the total iron result, (#1 - #2) = #3 (Oxidized Fe). Ferric iron forms an orange-red color in water and when it precipitates it settles out in the distribution system. If ferric iron is present in water supplies it can be filtered and removed before it passes into the system. Low levels of ferric iron may break through filters into the system during regular flow and it should be flushed regularly from fire hydrants. No flow/stagnant water conditions or corrosion reactions, may allow ferric iron to be reduced back into ferrous iron which directly demands more of the chlorine residual, re-generating rusty water further along in the system. System ‘dead-end’ conditions and unflushed fire hydrants can create oxygen-starved (anaerobic) zones that allow microbial iron to ‘migrate’ back into the flowing oxygen- rich water environment, creating additional dirty water throughout the system. Iron and color can be chemically controlled by maintaining a free polyphosphate residual in the distribution system and by flushing fire hydrants.
Copyright 2007 Spon Water Consulting, LLC.
All Rights Reserved
||Some customers called to say "the water is good now" After Bob optimzed the pre-chlorine dose our membrane filters remove 50% more Mn
- Mike B., IL